NFPA Compliant Assemblies Using VaproShield Membranes
Atlas EnergyShield Systems
Dow Thermax™ Rigid Insulation
FunderMax m.look Grey Core with Hunter Xci Rigid Insulation
Owens Corning - Various Wall Assemblies
Rmax Exterior Wall Systems Designs
Stonewood Phenolic Panels
Trespa Meteon Panel Systems
Hunter Xci and VaproShield Membranes in Various Assemblies
Xci CG and Xci CG (Class A)
Xci FOIL (Class A) and Xci A286
Xci Ply and Xci Ply (Class A)
An alternative to NFPA 285 full wall fire testing can be provided in the form of a limited engineering analysis or Engineering Evaluation provided by an engineer familiar with the NFPA 285 test and is knowledgeable in the field. This evaluation is based on the burning characteristics of a product as determined by ASTM E1354 “Standard Test Method for Heat and Visible Smoke Release Rates for Materials and Products Using an Oxygen Consumption Calorimeter.” Values determined by the E1354 test are compared to that of the similar material used in the original NFPA 285 test.
Engineering Judgment Letters Available
For specific commercial projects, if an existing NFPA 285 assembly test is not available, VaproShield will work with our fire consultants to provide an engineering judgment letter. In most cases, VaproShield will absorb the cost of acquiring the Engineering Judgment Letter.
Exemptions for NFPA 285 Testing
In the 2015 International Building Code, Chapter 14 Exterior Walls, the following exemptions are provided as an alternative to the NFPA 285 acceptance.
1403.5 Vertical and lateral flame propagation.
- Walls in which the water-resistive barrier is the only combustible component and the exterior wall has a wall covering of brick, concrete, stone, terra cotta, stucco or steel with minimum thicknesses in accordance with Table 1405.2.
- Walls in which the water-resistive barrier is the only combustible component and the water-resistive barrier has a peak heat release rate of less than 150 kW/m2, a total heat release of less than 20 MJ/m2 and an effective heat of combustion of less than 18 MJ/kg as determined in accordance with ASTM E1354 and has a flame spread index of 25 or less and a smoke-developed index of 450 or less as determined in accordance with ASTM E84 or UL 723. The ASTM E 1354 test shall be conducted on specimens at the thickness intended for use, in the horizontal orientation and at an incident radiant heat flux of 50 kW/m2.
VaproShield’s RevealShield SA Self-Adhered meets the exemptions of 1403.5. with a heat release rate of less than 150 kW/m2, a total heat release of less than 20 MJ/m2 and an effective heat of combustion of less than 18 MJ/kg and a flame spread of 0 and a smoke developed index of 75.